Extractor fan wiring
This article describes how mains powered extractor fans of the type often found in bathrooms and shower rooms can be wired.
Extractor fans in bathrooms are frequently powered from a lighting circuit. This is because many include a "run on" capability that is triggered by the operation of the light switch, and it not permitted to have a device powered from two separate circuits. Also UK bathrooms have traditionally not included power sockets, so its common to not have any general purpose power circuits available in the room.
This article describes the wiring schemes for a number of fan types and applications.
Note also that there are additional rules that apply to Bathroom electrics, and these must be followed for all fan installations.
Fans (especially those that may be operated by automatic controls) should be fitted with an isolation switch that will interrupt all live conductors (i.e. including neutral). This is to allow safe cleaning and maintenance of the fan. If the isolator is not visible to the person working on the fan, then it should also allow a facility to be "locked off" to prevent someone re-enabling it while work is being carried out (many isolators now include this capability as standard).
Some fans may also need additional fused protection beyond that provided for the circuit as a whole (e.g. at 3A), so you may need to include a fused connection unit in the feed to the fan. Consult the manufacturers instructions.
Types of fan
Basic manual fan with no timer
This is the easiest to wire. It is either run from a separate on / off switch (typically a pull switch) or perhaps a delayed action switch such as a vacuum switch, or can be connected in parallel with the lamp in the room such that it comes on whenever the light is on. Unlike other fans installations, it does not need a permanent live connection.
Fan with run on timer
This type of fan is very common. It will typically start operating when the light is switched on, but then continue to run for a pre-set time after the light is turned off. Thus "clearing the air" in the room.
More sophisticated examples may include a "delayed start" facility where it does not start up until the light has been on for a certain length of time. So the fan would not run for short trips to the bathroom, but would start running for longer ones. These are ideal for installing in places like en-suite bathrooms where fan noise might be undesirable at night.
Some fans even include a "timed refresh" mode, where they can be set to run periodically through the day - at pre-set intervals and durations. This is intended vent stale air from rooms with no natural air circulation.
Fan with humidistat
Humidistat fans are triggered by the level of moister in the air. Thus they respond when the air gets steamy, and run until the humidity level is reduced. Fans are available with a built in humidistat, or alternatively, and external humidistat can be connection to other types of fan.
Fan with multiple triggers
In some cases it might be desirable to include more than one type of control for a fan. Say to have timed run on operation for clearing smells from a bathroom, and additional humidistat control to reduce moisture and dampness in the room at other times.
The best place to take an electrical feed for a fan from is often a ceiling rose or junction box where the main lamp fitting is connected. This has the advantage of having all the connections required available in one place. Normally a Cables#3.26E cable would be used for this.
This wiring plan will simply run the fan when the room light is on. It can also be adapted for separate switching if required. Options include a manual pull switch, and a Vacuum time lag switch. The time lag switch will allow the fan to be manually started, but then run for a pre-set time. These manual switches have the advantage of needing no power themselves, and so will run with typical light switch wiring, and are compatible with all lamp types. (electronic time switches often need to bleed a small amount of power through the lamp to self power. These often cause odd behaviour with compact fluorescent, LED and other very low energy lamps)
Fans with a timer
This plan is ideal for timer fans triggered by the lighting circuit. The three pole isolator switch allows for interrupting both the switched as well as the permanent live and neutral connections.
Fans with a built in humidistat
These can be simply connected to a permanent live and neutral (via an isolator). They will then run entirely under the control of the built in humidistat.
Fans with timer and humidistat
This is the simple version of the circuit. Note that the alternative version may be required below of you find that you humidistat also turns on the room light when it runs the fan.
The more complicated switching arrangement disconnects the link to the switched live of the lamp when the humidistat is active. (you can also achieve the same result by using a double pole light switch, and using the second pole only for triggering the fan - however that is less easy to retrofit in many cases since the wiring required will not be in the drop to the wall switch).
Since the above circuit includes a relay, additional transient suppression is included to prevent large voltage spikes generated when the relay coil is energised or powered off. This will protect the electronic circuitry on the fan. Consult the manufacturers instructions about what level of spike or transient suppression is required. (many will stipulate that protection is also required if the fan shares a circuit with traditional linear fluorescent lamp fittings, since these have an inductor used as a ballast, and this may also generated voltage transients).
Using relay controls
The above photograph shows a relay, with a typical 0.1uF/100 Ohm RC suppressor, and a 250VAC "MOV" transient suppressor assembled into a wago box. This is intended to be lost in a void somewhere (i.e. near the fan or its switch) in the fan installation and connected to the circuit via its attached lead.
Commonly the isolator switch makes a good location to include all the necessary terminations.