Safe zones for electric cables
Electric cables are usually run in one of a number of prescribed safe zones. Knowing where these zones are allows you to correctly install cables and help eliminated damage to them when drilling walls at a later date
The safe zones for cables concealed in walls are
- a horizontal zone within 150mm of the top of a wall
- a vertical zone within 150mm of the angle formed by two walls - e.g. internal and external corners.
- the horizontal and vertical zone adjacent to an electrical accessory (switch, socket, cable outlet etc)
- where an accessory on the reverse side of the wall can be easily determined, e.g. through a door or archway, and the wall or partition depth is 100mm or less, then the horizontal and vertical zones to that accessory apply to both rooms:
Where cables are not in installed in a safe zone then they need to be installed according to the rules explained here.