Difference between revisions of "Install Bar Shower Valve - in solid wall, copper pipe"
(sealing the holes between tails and board in hollow wall installation)
m (Installing a Bar-type Shower Mixer Valve moved to Install Bar Shower Valve - in solid wall, copper pipe: splitting article)
Revision as of 01:20, 1 March 2008
Bar-type thermostatic shower mixer valves are cheap and readily available. However they can be fiddly to install. This article describes methods of installing them into solid and stud walls.
Make outlet elbows as shown with:
- 3/4" BSP male X 22mm solder fittings
- 22mm street (spigot) elbows
- 22mm X 15mm reducing couplers (fitting reducers could be used directly into the elbows instead)
The pipework should be pressure-tested before installing.
Make a former out of board of approx same thickness as tiles+adhesive will be, with holes at 150mm centres. Fit pipework to shower valve through the former.
Bend the pipework as necessary: in this case they will emerge under the bath
Wrap the board in plastic so that it doesn't get stuck to the plaster: it will be removed after the plaster has set.
Having chased the wall, plaster in the pipework. One-coat plaster is suitable, although browning or bonding should be OK as long as it isn't too stiff to push out as the pipework is pushed into it.
If mortar is used the pipework must be protected from corrosion by wrapping it in e.g. PVC tape, but note that the wrapping material must not be too resilient as the pipework is being used to hold the mixer valve in place.
The ideal is to fill the chases behind the former so that the plaster squeezes out when the pipework assembly is pushed into it and holds the pipework firmly when set. If the plaster doesn't squeeze around the pipework it will be necessary to apply more plaster when the former comes off.
Masonry nails (approx 50mm) driven partway through the former at angles hold it in place while the plaster sets. Ensure that the valve is pushed back tight onto the former. (A couple of hook eyes fixed into the former and some string looped through to hold the valve would do this.)
Set the chromed bezels about midway in their travel along the threaded fittings to allow ajustment to the actual depth of the tiling.
Ensure the valve is set truly horizontally!
When the plaster is set disconnect the valve and remove the former board. Apply more plaster if necessary to hold the pipework firmly in the wall, and to achieve a surface flat enough to tile onto.
Connect up the pipework:
Tile, and fit the shower valve:
Make fittings as shown with:
- 3/4" BSP male * 22mm solder fittings
- 22mm * 15mm solder reducing fittings
- 15mm solder * 1/2" BSP male fittings
- 1/2"BSP * 15mm compression wall plate elbows (If copper pipe were used solder-type elbows could be used.)
Cut a piece of 18mm WBP ply to fit between studs of the wall. Make cutouts at 150mm spacing in the ply and screw the wall plate elbows to the wood.
Fix the board to the studs and connect the pipework to the elbows.
Pressure test the pipework.
The wall can now be boarded over with the threaded tails protruding through holes in the board to the right depth for fitting to the shower valve after tiling. The gap between the tails and the board can be sealed with a suitable mastic, and/or sealant applied to the conical chromed bezels of the shower valve to prevent water running into the holes.