Crimping electrical cable joints
Note that this article refers to the jointing of electrical cable in fixed wiring installations, not for extending flexible cables connected to appliances
Acceptable jointing methods
There are various situations where it may become necessary to join an electrical cable, such as when effecting repairs and upgrades to installations. The wiring regulations basically allow for four methods for making cable joints:
- Screw terminal connections
- Joints produced by a compression tool (i.e. Crimped)
- Soldered Joints
- Welded Joints
1) is most commonly used in electrical accessories such as switches and sockets. However this method is only acceptable where the joint will remain accessible for future inspection and maintenance, since screwed terminal connections can become loose over time.
4) Is not an option readily available in many domestic situations. Hence if one needs to make a joint that is robust, and can be safely entombed into a building we are left with 2) & 3).
Crimping is a quick and reliable method of jointing that is easy to deploy in the field since unlike soldering it does not require time to be spent waiting for a soldering iron to heat up, and poses no burn risk to the operator when working on confined spaces.
Required Tools and Materials
For making reliable crimped joints the correct crimping tool must be used. Adequate crimping tools are of a substantial contruction and include a ratchet tightening mechanism that ensure adequate pressure is applied to the crimp before it is released. A suitable tool is available from most good tool shops and electrical retailers such as this[].
Crimp terminals are available in a number of sizes and two basic types: [Insulated] and [Uninsulated]. Both types can be used, but the procedure is different, and uninsulated crimps require the use of a different crimp tool to insulated ones. For the purposes of this article we will use insulated crimps since these are the more commonly available, and require a little less work to use.
In addition to a crimp tool you will need a few basic tools like wire cutters, and strippers. You will also need some heatshrink tubing of a size appropriate for the cable to be joined
The wrong tool for the job
Note that the cheap non ratchet crimp tools like this are not suitable:
If you have one of these, save it for stripping wire and cropping small bolts.
The crimping procedure
Let's assume we need to repair a section of cable. For this example we will use a section of 2.5mm² T&E that has had an unfortunate encounter with a chisel!
Prepare the wire
The first job to do is cut the wire and cut out any damaged section:
Strip the cable back a couple of inches (about 50mm) on each side so that there is room to work.
To Reduce the size of the overall crimp, and to make for a neater joint, the lengths of wires can be staggered so that the crimp terminals will not form a bunch:
Before going any further fit the insulation!
Cut some heatshrink to a length enough to not only cover the joint but also extend an inch of two down the cable. This will make the final joint more moisture resistant. (If waterproofing is important then an adhesive lined heatshrink can be used):
Also remember to fit sleeving to the earth wires. Slide the heatshrink it up one of the wires until it is out of the way:
Select suitable crimps
The crimp selected needs to not only match the wire size in question, but also have enough current carrying capacity for the circuit. The Blue crimps used here have the following spec:
- BLUE 32A BUTT SPLICE (100/PACK)
- Area, wire size min:1.04mm²
- Area, wire size max:2.63mm²
- Current rating:27A
- Material, contact:Copper
- Material, insulator:Coloured Vinyl
- Plating, contact:Electro-tinned
- Temp, op. max:85°C
- Temp, op. min:-20°C
- Voltage rating, AC:415V
Position the crimp in the jaws of the crimp tool (in the recess marked with the same colour as the crimp), and squeeze gently so as to grip the crimp without squashing it:
You should position the crimp so that the active part of the jaws are directly over the metal part of the crimp, leaving the empty part of the plastic insulation sticking out
Insert the wire such that the insulation is tucked inside the shrouded part of the crimp:
Once the crimp is made, inspect the crimp to ensure it looks correctly compressed and the wire is still in the correct place with no uninsulated section showing. Attempt to pull the wire out of the crimped connection to verify that it is held properly:
Repeat for the other wires in the cable:
Finally complete the crimp to the other cable:
Once the cable is joined, you can test your work. As described above the first test is mechanical: that the wire should not pull free of the crimp when applying reasonable force.
To test electrically, find where the cable you have repaired connects to the exiting circuit at both ends. Disconnect both and twist the wires at one end together. Now use a multimeter on a low ohms range to measure the resistance between each wire. See the section on Test procedures in the Elctrical Circuit Faults article.
Last job is to slide the heatshrink over the joint and shrink it:
Heatshrink is best shrunk with a small purpose made hot air gun. If this is not available a gas flame can be used, but it must be played over the joint very quickly and sparingly so as not to scorch it.