Bad Ideas - Electrical
Things to Avoid Doing!
- 1 Single whole house RCD
- 2 Freezer sharing RCD with half the house wiring
- 3 Plugin electric heating
- 4 Historic rubber wiring
- 5 Disturbing historic rubber wiring
- 6 Fitting a mains drill with an RCD
- 7 Showers wired on 2.5 mm^2 T&E
- 8 Showers that give you a tingle or shock
- 9 Plastic waterpipe earth
- 10 Local earth rod & no RCD or ELCB
- 11 High Tech Appliances
- 12 Colour code madness
Single whole house RCD
A single appliance earth fault, or assorted non-fault conditions, will cut your whole supply off. Not very good if you like lights and a working freezer, and don't have Sherlock Holmes on hand to figure out where in the system the problem lies.
Freezer sharing RCD with half the house wiring
Any RCD trip is liable to ruin your freezer contents. A common setup in new installations until very recently, unfortunately.
Plugin electric heating
One of the most expensive heating methods of all. Can also lead to overloaded sockets and extension leads, causing a fire risk
Historic rubber wiring
Old rubber wiring is regularly very badly perished, leaving bare uninsulated wires intertwined in unsuitable places. High risk of fire and shock.
Disturbing historic rubber wiring
A quarter inch of movement is enough to cause a short where wiring is badly perished. Shorts cause shock and fire, or blow supply fuses. Historic rubber wire should normally be left alone until replacement, unless it can be verified that the insulation is still in one piece.
Fitting a mains drill with an RCD
...in the mistaken belief that this offers some protection if you drill into a live wire. It gives no such protection, but encourages less care to be taken over where one drills, thus increases the danger.
Showers wired on 2.5 mm^2 T&E
Showers that give you a tingle or shock
There are normally several layers of protection against this occurring with showers, if a shower reaches this point the installation is in a terrible state and may fry you at any time. All users of such showers are automatically nominated for the prestigious Darwin Award.
Plastic waterpipe earth
Houses generally used to use the metal supply waterpipe as an earth, and a good earth it was. But today many water supplies have been replaced with plastic pipe, which may leave the house with no earth connection. This is a real shock hazard.
Local earth rod & no RCD or ELCB
Common on 1950s installs and older, but sometimes found on much more modern systems. Often results in no effective earth protection, as earth fault currents will neither blow a fuse nor be kept down to a safe voltage by the earth rod.
High Tech Appliances
Colour code madness
Behind this Spanish socket lurks madness. The middle pin (red, white) is earth, and the green/yellow striped wires are both live & neutral. So of the 2 red wires, one is earth the other live.